[OZAPRS] UIDIGI 1.9 problem?
owen at owenduffy.net
Thu Oct 16 21:46:39 EST 2014
Keep in mind that if you can read the existing EPROM, you can use
UIDMPCFG.EXE to dump the configuration, including password.
Swapping TNC means setting up modulation level using appropriate test
equipement... well it should but it seems practice is "all knobs to the
right". Given that, it might be deserving of a review of modulation
I can hear three digis here, and peak deviations are 1.5, 6 and 10kHz...
should be 3.
On 16/10/2014 20:41, Peter VK2MPJ wrote:
> I am thinking that this maybe the case. I am thinking a replacement
> TNC programmed up ready to go will be the best option here.
> I think I have access to an EPROM burner, but will keep your offer
> in mind, thanks Scott.
> Pete VK2MPJ
> On 16/10/2014 8:01 am, Scott Evans wrote:
>> Sounds like the txt file you've been given differs from the actual
>> configuration. The only way to get around that is a site visit to
>> connect directly to the tnc and reconfigure. However it's probably
>> best to arrange a new EPROM with the necessary alterations! If you
>> don't have access to an EPROM writer contact me off list and we can
>> arrange one to be written as I've got a little white box here
>> (somewhere) and I can do it for you and mail it to you.
> OZAPRS mailing list
> OZAPRS at aprs.net.au
More information about the OZAPRS